In-Ground
ID : 4146
LED 3000K, 4000K, 6500K 240Vac CRI >80 MacAdam step 3
Input power : 9W
Dimension  Ø116 x 153 mm
Light Distribution : Symmetrical ( Honey Comb)
Electronic driver ON/OFF
CE and BIS

LUMINAIRE TYPE
Wall Mounted luminaire. IP rating IP67
MATERIAL CHARACTERISTICS
Die-Cast aluminium alloy housing (grade ADC12 with test certificate). 316 grade stainless steel front ring. Silicone clear gasket. SS fasteners. Mechanical resistance IK09.
Pure polyester powder coated process : Acid treatment & pure polyester powder coating.
INSTALLATION AND MAINTENANCE
ABS plastic installation housing for preparing the recess opening in ground. The luminaire are fixed in recess installation housing by stainless steel screws.
LIGHTING PERFORMANCE
Toughened Clear glass diffuser of 8mm thickness with optical reflector & honeycomb to reduce glare controlled.

This luminaire contains built-in LED modules. LED modules are engineered accordingly to the existing regulations of Lumen Maintenance (LM80) and Technical Memorandum (TM21), Lifespan of the luminaire > 60,000 hours at 40°C. Operating ambient temperature range is from -15°C to +50°C. Driver efficiency >85%, power factor >0.9, THD <10%, Surge protection 2.5KV. 